- May 23, 2016
- Reaction score
- Yukon, OK
Here you go...I looked on Amazon and only see steel ones, BRS has some for like $50
The flow restrictors are the same for the 75 and the 150 gpd. Since it is just an additional 75 gpd membrane. They use the 550ml restrictors. The 100 gpd membranes use the 800ml restrictorsI knew there was something missing. The flow restrictor. I know BRS has an old video on converting a 75gpd unit to their 150gpd water saver unit. I watched that to upgrade my rodi.
To have the ASOV work, you must have check valves on the permeate lines coming out of each membrane.Sometimes those 90 connectors on the membranes can be "check valve" style. Could be faulty as well. The setup should be into the sediment first, then carbon block(s), ro membranes plumbed in series for water savings. (Waste line of first membrane into the input of the second membrane then into your di cartridges.
Hmm. The challenge with needle valve restrictors is that it is a pain to dial in the correct permeate to concentrate ratio in the absence of flow gauges (which none of these little systems have). Every time you open a needle valve to flush, then you'd need to spend the time to dial it back in. Not practical. Better to use a ball valve bypass and open it to flush.Plus, flushing your RO membranes is super easy with the needle valve as all you need to do is open it up all the way to flush em.
Again... one of the reasons I'm not a fan. This is not how any of this is supposed to work!The flow restrictors are the same for the 75 and the 150 gpd. Since it is just an additional 75 gpd membrane. They use the 550ml restrictors. The 100 gpd membranes use the 800ml restrictors
I will give you a call around 1230 central time, if that works for you.There are some plumbing issues that I saw in the pics. Would be best if you gave us a call when you are in front of the system.
When I tested my system before this post my PSI was way low so I thought it was my house pressure. Come to find out it was not having any flow restrictors plumbed in so PSI wasn't able to build up.Why do you need a booster pump if you house water pressure is 90 psi?
What do you recommend then for using two membranes? Or would it be better just to have one?
What do you mean by that this is not how any of this supposed to work? The way we use our RO systems?Again... one of the reasons I'm not a fan. This is not how any of this is supposed to work!